Refrigerated panel floor, the same thickness as the walls and ceiling. It is ideal for the transit of people and manual trucks on 4 non-metallic wheels with a rolling load of less than 400 kg and 4,000 kg/m2 of evenly distributed static load. The interior finish is reinforced with a non-slip birch and phenolic plywood. It does not support pallet trucks, forklifts, stackers, etc.
Stainless 0.8 mm non-slip foor
Similar to the reinforced non-slip floor, which incorporates a stainless steel sheet finish with non-slip marking.
It opens out of the cold room. Its height must be 10 cm lower than the internal height of the cold room, as minimum.
It moves laterally around the outside of the cold room. It is necessary that its height is 30 cm lower than the height of the interior of the cold room, as minimum.
Measurements of useful passage of the hinged door.
The standard size door can be installed on any cold room wall that is at least 1.32 m long. The door comes assembled and adjusted on one of the panels.
For other measures, consult.
The height of the sliding door must be a maximum of 30 cm lower than the internal height of the cold room.
In addition, there must be a paneled side space next to the door opening of at least the value equivalent to the door opening plus 50 cm.
Opening direction of the door:
Select the opening direction of the cold room's door: to right or to left.
Select if you want lock on the door.
Strip curtain swing:
Select if you want to include a strip curtain in the door of the cold room, with stainless steel support and made with materials suitable for the food industry.
It is advisable to use a strip curtain, as it improves the functioning of the cold room and favors energy saving.
Compact wall-mounted EMB/EMC
It is installed on a wall of the cold room, quick and easy to mount. It is necessary to locate them in a place with good ventilation. Also available with a centrifugal condenser, to evacuate the hot air to the outside.
Compact ceiling-mounted EMR/EMF
It is installed on the ceiling of the cold room, quick and easy to mount. It is necessary to locate them in a place with good ventilation. Also available with a centrifugal condenser, to evacuate the hot air to the outside.
Commercial split ESC/ESF
Type split monoblock, the evaporator is installed inside the cold room and the condensing unit outside. Also available with a centrifugal condenser, to evacuate the hot air to the outside.
In freezing chambers the panel thickness must be 100 mm.
In freezing chambers the thickness of the panel must be 100 mm.Pressure balancing valve. It is necessary in freezing cold rooms.